I am trying to replace the faucet in my tub,
But the brass fitting it screws onto is larger than all of the standard size one's.
When I measure the plastic thread hole in the old one, it measures 1 1/4" (inches)
Thank you for your question, JJWeb! RP17453 connects by either sweating onto 1/2" C.W.T. (copper water tube) or threading onto 1/2" IPS (iron pipe size). If your previous tub spout was installed onto another manufacturers adapter, this will need to be removed before using this tub spout.
Best regards, Edward
Date published: 2018-05-22
How long of a 1/2" pipe stub is needed for the adapter?
The distance from the wall to the end of the 1/2" copper pipe on my bathtub is 1 1/4". Is this long enough to use with the brass adapter that comes with this Delta tub spout? If not, what is the recommended way to install the spout? I looked on-line for detailed installation instructions, but could not find any.
Hi AW, Thank you for your question. You will need at a minimum 1-1/2" and preferably 1-3/4" of copper to solder on the adapter. The only other option is if you can solder on a 1/2" copper male adapter keeping your overall length to 1-1/4" at the maximum, 1/2" at the minimum and then threading the tub spout adapter on.
Date published: 2013-10-30
will the spout work for my situation explained below?
My 1/2" copper pipe extends exactly 4" from the wall and has threads on the end. threads are 1/2' long. will the spout thread onto the pipe and be tight against the wall and be facing down?
Thank you for your question, Jack. The tub spout will thread onto a 1/2" pipe that extends 5/8" to 1 5/8" from the finished wall or sweat onto a 1/2" copper pipe that is 2" to 4".
Date published: 2017-11-24
I have an old Delta Tub spout that screwed on using this fitting will it fit on this?
Here is a photo of the old "stub" that is sweated on to a copper pipe. This is a 25 year old Delta 600 series tub set. I would like to fit a stainless steel tub spout on this without removing and replacing. Open to other spout models in stainless.
Thank you for your question. Delta Faucet model # RP17453SS can either be sweat onto a 1/2" copper pipe or threaded onto a 1/2" iron pipe. It does include an adapter assembly.
Date published: 2014-09-28