Cassidy Shower Only with R10000-UNWSHF
I would like to maximize water flow and I like the Cassidy trim. From the FAQ it looks like the R10000-UNBXHF provides more flow than the R10000-UNWSHF. Will these valves work with the Cassidy cartridge? The water line is 1/2 inch CPVC. Thanks for any help.
Hi Autopilot3, Thank you for your question. The R10000-UNWSHF, and the R10000-UNBXHF multichoice universal roughs will both work with the Cassidy cartridge. The inlets and outlets of the valve are 1/2" MIP.
Date published: 2016-03-08
Since I already have two R10000 shower only with stops, can I use both to run two shower heads without the need for a diverter?
The two new valves were given to me and I want to utilize both. Can they be installed to run two shower heads?
Thanks for your question. You may use two R10000 valves to control two shower heads without a diverter valve. This will allow each shower to have separate volume and temperature control.
Date published: 2017-06-06
R10000-UNBXHF and R10000-UNWSHF flow rates
Have a shower only install going in. Seeing some what I think is conflicting Q&A answers on flow rates of the R10000-UNBXHF and R10000-UNWSHF (one Q&A response was no difference in flow rates, but Delta Rep today told me the UNBXHF had slightly higher flow rates than the UNWSHF valves).
Can you please confirm the flow rates for BOTH HF valves (@ 60 and 80 psi) using:
Monitor 17 dual function PB and TempAssure 17T dual function thermostatic cartridges?
Thank you for your question. These are the maximum flow rates from the shower port:
-- 17 Series --
R10000-UNBXHF - 6.6 gpm @ 60 PSI. 7.7 gpm @ 80 PSI.
R10000-UNWSHF - 5.9 gpm @ 60 PSI. 6.8 gpm @ 80 PSI.
R10000-UNBXHF - 8.6 gpm @ 60 PSI. 9.9 gpm @ 80 PSI.
R10000-UNWSHF - 7.4 gpm @ 60 PSI. 8.6 gpm @ 80 PSI.
Date published: 2016-07-17
Any limitation as to how far this valve can be from the 6 setting diverter, Delta R11000, Delta T11953? We are planning to put the valve at entrance to shower maybe 5 or 6 feet away from where jets/shower head would be and want to put the diverter there
Hi, Ray R!
Thank you for your question. The Diverter valve, R11000 and trim kit, T11953 can be installed anywhere you desire. There is no measurement limitations for where the diverter valve/trim kit should be.
Date published: 2018-04-12
I installed R10000-UNWSHF Rough in. I am using Schluter Kerdi board and the Schluter mixing valve seal for both my rough in and diverter rough in. Can the Delta Plaster guard be removed, the Schluter mixing valve seal will be superior for leak prevention.
Thank you for your inquiry! The Delta MultiChoice Universal Rough-In Valve R10000-UNBX contains a plasterguard that is used in aiding the installation of your faucet. It is not necessary to the functionality of the faucet. If you choose not to use the plastergaurd as a guide to cut the hole, please make sure that the hole is large enough to access the screw holes for the trim plate.
Date published: 2018-04-09
3/4 PEX to 1/2 NPT Ports
Can I connect 3/4 PEX to the 1/2 NPT ports?
Thank you for your question. You may connect PEX tubing to the valve with the correct adapters.
Date published: 2017-02-28